ANDOVER NETCONTROLLER PDFJuly 25, 2020
Find great deals for Andover Controls Continuum NetController LL Cx Tac Inc.. Shop with confidence on eBay!. Andover Continuum™. Product Catalogue. Issue: October . Infinet NetController II CPU Module. Infinet NetController – Display Modules. NetController II Andover Continuum power supply or third-party UL Listed UL Be sure your Andover Continuum cabinet is connected to the ground.
|Published (Last):||26 June 2007|
|PDF File Size:||8.22 Mb|
|ePub File Size:||20.6 Mb|
|Price:||Free* [*Free Regsitration Required]|
Results 1 to 10 of Andover Controls Net controller problem.
Thread Tools Show Printable Version. Ping to the controller always didn’t lost. In same network we have other controller Andover CX with them we have not problems.
First question is what version of Continuum are you using? I’ve seen this problem before. There is an error in the stored SQL database for that controller. Go back andovdr and do a explorer refresh. The controller should be gone at this point. Next create a new network controller, do a teach.
Andover Controls Continuum NetController LL Cx-9680 Tac Inc.
If controller is functioning properly it should come back online totally blank. Send the controller to the SQL database this, should be fairly quick as there are no programs or points in the controller.
Note the values netcontgoller the errors and freemem system variables.
Set send to controller options to “reload attached objects, but not attached controllers”. Do a “send to controller”.
Andover Continuum NetController II – Feature Blast | Schneider Electric
This should reset the controller, wait for it to come back online, then send the system variables to the controller. If all is good at this point your controller is good. Import the previously saved text file, Send to controller and all should good.
One last thing, check to see if all the programs and functions are correct and match the text file. Netcpntroller of Continuum is 1. Thanks for your help, as soon as possible i will try to do what you said.
Netcontrooller i noticed, that actually the problem not only with the Net Controllers but with some Site Controllers I think that this is also database problem, because i think controller work in “NoDB” mode, but may be i wrong. I hope you can help me solve this problem. I am very sorry, I’m not very good at English. Thanks you Very much. Sorry, one more question, how to send data to controller from text file?
Originally Posted by borias. If we evolve from the monkey then why are there still monkeys.
Hello, I have a problem with Andover Controls Net controller: Originally Posted by AutoPilot. Borias, From your question about saving a text file I’m wondering if you have had any formal Continuum Training.
This is not a DIY board and what I suggested is not for the faint of heart. Call your controls contractor. When you reload the controller, the proper path, and handle info is sent to the controller. If all is well, the controller netconfroller be ready to reconcile any handle issues it the text dump. If you get any errors during the text import, you will need to correct them. I usually remark the error lines out until I a clean import. After a successful import no errors you should be able to reload the controller without any problems.
Andover Continuum NetController II – Feature Blast
I only do this on controllers that have the problem Borias described. I have been unable to find the cause for the SQL database corruption.
It’s rare, difficult and time consuming to trouble shoot. I have made all had told Autopilot. But at a stage when I send blank controller to SQL database, in the distributions window i get error produced: Ameya Hi Autopilot, I am new to the forum and I am looking solution for somewhat similar problem.
After creation of network I learn controllers. It takes around half an hour to learn. I could see my controllers online. All three controllers are online and reply for ‘who is’ global broadcast. Even i tried to delete nw and everything which i have created.
But problem still exists. Please can you tell me what could be the problem??? I am using continuum version 1. General Discussion Pro’s Forum: Oil Burners Pro’s Forum: Building Science Discussions Pro’s Forum: Training and Education Pro’s Forum: Valves, Regulators, Filters, Etc.
Power Quality Pro’s Forum: Getting Pumped for ! The Thrill of Exceeding Expectations. Building Success with Routines and Rituals. Subscribe to this feed. Related Forums The place where Electrical professionals meet.
Then One Foggy Service Call All times are GMT The time now is HVAC-Talk is proudly provided by: Results 1 to 10 of 10 Thread: I haven’t done what Autopilot has discribed.
But I woul like to try them. First you have to go to the Menu bar forgot the term at the bottom right and find the controller ICON. Like Borias we sometime encounter the same problem. But I need clarification. Like you we have version 1. Did it kept the infinity ID number, IP number, all other number that it needed? I’m asking this question because I haven’t done it. I have done some reloading, created points, revise the program but not this deep of situation If we evolve from the monkey then why are there still monkeys.